|FA163719||Are Series Rating available for QO Main Lug Only, 1 Phase load centers when using std QO 10,000 AIR branches ?|
Series Ratings for current design Series S01 and S02 (Convertible Mains), 125 - 225 ampere, Main Lug Only, 1 Phase QO load centers include:
|FA163611||Can you do a multipoint addressing with the ATV312 drives?|
It is not possible to do multipoint addressing with the ATV312 drives. The menu for the configuration can be displayed on the remote HMI but...
|FA163564||Can a NQ, 84 circuit 400A panelboard be provided with a sub feed breaker? |
No, we do not offer a box larger enough to accomadate a sub feed breaker kit in a 84 circuit NQ Panelboard.
CTA-ID : 2055122
|FA130908||Is the Zelio Smart Relay software - SR2SFT01 compatible with Windows 7?|
The software is compatible with Windows 98, NT, 2000, XP, ME and Windows 7. CTA-ID : 2055098
|FA162393||How many S29450 can be mounted in a PGL breaker?|
It has place for (3) auxillary contact and (1) alarm switch and (1) overcurrent switch.
CTA-ID : 2061081
|FA162181||What is the replacement pullout only for a FTL2100?|
4050704950, The replacement pullout is OBSOLETE and NO LONGER AVAILABLE.
CTA-ID : 2060765
|FA116066||Is there a restriction for a breaker mounted opposite 125 amp ED, EG, or EJ breakers?|
Yes, the ampacity of the breaker mounted opposite cannot exceed 20 amps. CTA-ID : 2027586
|FA115737||How many EDB34125`s can be installed in an NF panel?
If enclosure is a NEMA 3R , just one can be mounted in 400/600A panels. If box is a NEMA 1 ,more than one can fit in a 400A/600A panel . If 125A...
|FA162002||REJECTED: THIS INFORMATION IS STILL NEEDEDAre KA/KAL 2 pole breakers rated for use at 250 Vdc?|
REVISION TO RESOLUTION 2023187: KA/KAL BREAKERS ARE NOW OBSOLETE.
Yes, 2 pole breakers are good for 10k AIR at 250v DC. Note the 3p breakers can...
|FA113738||Can you rotate the NF panel for opposite feed?|
Yes, turn the panel interior 180 degrees. If the panel has a vertically mounted main breaker turn it 180 degrees also. Turn the branch breaker portion...