|FA167602||What is the ATS22 adjustable range for ILt, current limit?|
The range is 200% to 700% of parameter In, motor rated current. The maximum is limited to 350% of the ATS22 amp rating.
If the application requires...
|FA167597||How can you change the monitoring screen to show different parameters other then frequency reference on the ATV61 and ATV71 drives?|
Under Main Menu,
Go into Menu 6 Monitoring Configuration.
6.2 Monitor Screen Type adjusts the number of parameters that can be displayed and the...
|FA167444||What are the Micrologic 5.0P ground fault alarm pick up and delay ranges?|
Pickup: 20 to 1200 amps, +/- 15%.
Delay: 1 to 10 seconds
CTA-ID : 2062500
|FA167414||Do you have to derate the ATS48 Soft Starters if you mount them at high elevations?|
Maximum operating altitude
3300 feet without derating. Above this, derate the nominal current by 2.2% for each additional 330 feet to the...
|FA167056||How can ATS22 be set for Freewheel Stop mode? |
Goto SEt menu and program dEC parameter to Free.
|FA166888||ATS22 soft start is tripping on SnbF and this code cannot be cleared.|
SnbF indicates that too many starts were attempted based on the settings for parameters Snb (number of starts) and SLG (starts period). The soft...
|FA97528||Can the In Phase Loss on the 8803 Omegapak be turned off?|
This can only be done on the CT style units and is changed using the Commissioning terminal (8803 PPO1 ) or PC software (no part number). Go to the...
|FA166691||How is the ATS22 set for 3 wire control?|
Wire the momentary normally closed STOP contact to LI1 and the momentary normally open START contact to LI2.
Program the ATS22. In the I-O menu,...
|FA166743||How can the ATV61 drive be prevented from going into reverse when the HMI dial is turned to the negative range?|
In Menu 1.6 COMMAND, set RV Inhibition to Yes. This also applies to the ATV71 drives.
Note that this does not prevent reverse operation when the...
|FA166718||How can frequencies be skipped in an ATV61 / ATV71 ? |
In menu 1.3 Settings, adjust the following parameters:
Skip Freq = desired frequency ( in the middle of the skip range )
Skip Freq Hysteresis = (+)...