|FA149423||Was there a design change in the door operation on the HU365R Safety Switches? |
Yes in 2009 there was a design change to the HU365R safety switches, making the door operation from top hinged to becoming side hinged on the left...
|FA149425||What is the differences between the EZM31200GCBU and EZM31200GCBE Main devices?|
The EZM31200GCBU is a Underground ONLY feed, non-EUSERC, that comes standard with lugs.
The EZM31200GCBE is a Underground ONLY feed, meets the EUSERC...
|FA149424||What main breaker is used in the EZM31600JCBC and does the main breaker have an adjustable trip?|
The EZM31600JCBC includes a RJF36160U31A breaker and this breaker does have an adjustable Long time and Instantaneous settings.
CTA-ID : 2060284
|FA127070||Does Square D manufacture 15KV C/T`s?|
No ,these are not offered anymore . Try Trench Ltd. ( formerly Haefly Trench) in Canada or ITI - Instrument Transformer Inc. in FL .
|FA148759||Can Powerpact H, J, L, M, P, R, and Q frame circuit breakers be backfed? |
Per UL 489 paragraph 220.127.116.11 and NEMA AB3 paragraph 3.4, molded case circuit breakers are fully tested and UL Listed for reverse connection unless...
|FA148760||What is the lug wire range for an HLL36030M71?|
Lug kit AL150HD takes (1) #14 - 3/0 Al or Cu conductors per phase.
CTA-ID : 2060451
|FA148757||9007FA1: what grade is the stainless steel? |
Material is #302 stainless.
CTA-ID : 2060472
|FA148763||What is the Interrupting Rating for a FJ Type Breaker?|
The interrupting ratings for the FJ 2 or 3 pole breaker, 15-100A is 100K at 240V and 65K at 480V.
CTA-ID : 2060356
|FA148766||What is the suffix ``X`` on the Powerpact circuit breakers?|
That digit in the catalog number is for the rating plug. Since this trip unit does not have a rating plug, we use an `X` as a place holder.
|FA148756||Will the Kirk or Federal keylock for a Masterpact MP work on a Masterpact NW circuit breaker?|
Yes, just order the new provision for the NW, cat.# S48542.
CTA-ID : 2060471