|FA152209||Will the LDN36400CU33X breaker sense through the 13th harmonics? |
Micrologic trip units for the Powerpact H, J, and L frame breakers are true RMS sensing through the 13th harmonic.
CTA-ID : 2060577
|FA152210||What is the part number for a closing plate for the 8538 Series K Nema 1, 3R/12 enclosure?|
The closing Plate (for all round operators) is a 9001K51.
CTA-ID : 2060396
|FA152211||What is the difference between an XCKJ20541H7 and XCKJ10541H7?|
The XCKJ10541H7 is SPDT with, with positive opening contacts, 1 normally open and 1 normally closed contact and the XCKJ20541H7 is 2 SPDT with 2...
|FA152212||How can the AOC output terminal be set up as a logic output in an Altivar 31 drive?|
In the IO menu, set AOIt to 0A and then set dO to the desired logic output function such as rUn, Drive Running. The logic output state is 1 (24V)...
|FA152213||What class overload protection does the ATV312 drive provide?|
Based on this setting the drive provides class 10 overload protection.
You can set this overload parameter in the SEt menu under ITH which is based...
|FA152214||What is a good source of information for the ATV312 drive?|
Most information can be found in the following documents:
DIA2ED2090404EN is the catalog.
BBV46391 is the installation manual.
BBV46385 is the programming...
|FA152215||Does the ATV312 cooling fan run all the time?|
No. The fan starts automatically when the drive controller is commanded to run (receives a run command and a speed reference). It stops a few seconds
|FA152216||What are the part numbers for ATV312 DIN Rail mounting kits?|
There are 2 DIN rail mount kits to allow some of the smaller size Altivar 312 drives to be mounted to 35mm DIN rail.
Use VW3A9804 for ATV312H018M2,...
|FA152217||Can the Altivar 312 drive be set up to start with a run command active or to restart without requiring the run command to be cycled in the event of a power outage?|
Yes it can. If the drive is set for 2 wire control In the IO menu, set tCC=2C and tCt=LEL. The same logic will apply to the run reverse command.
|FA152218||Can the LUB32 use the smaller (less than 12 amps) control units? |
Yes, it can.
CTA-ID : 2060456