Can I get ground fault trip on a Masterpact NT/NW and then turn it off later?
No. To disable ground fault, you would need to replace the trip unit.
CTA-ID : 2007247
Answers which others found helpful
> Customer has a Masterpact breaker with an electronic trip unit which includes ground fault. They do not want ground fault. Can it be turned off?
> Customer has a Masterpact NT, which includes ground fault. They do not want ground fault. Can it be turned off?
> We are attempting to understand the implications of using LF or L1F arc flash NW`s in a selectively coodinated system. If we need to turn the Instantaneous OFF to coordinate, are we disabling the arc flash limiting properties of the NW?
Please rate the content of this information
What can we do to improve this information?
Your email address
> Submit Feedback > Cancel