...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Control Transformers may experience momentary overloads on high inrush loads
Applies to 9070 T and TF type Control Transformers by SquareD/Schneider Electric
Inductive loads such as Motors, Solenoids, and Transformers may produce high inrush currents when first energized
Transformers are 100% rated devices. As such, they do not have any continuous overload capacity. CPTs are specifically designed for momentary currrent draw in excess of it`s rating for high inrush type loads. For direction on selecting the appropriate CPT for an application, see page 5 of the Industrial Control Transformer catalog, document # 9070CT9901, attached below.
CTA-ID : 2003429
Sign up for all the latest solutions, offers and best practices straight to your inbox.