Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Differentiation between K4/K13 and HDIT type Transformers
Applies to K4 and K13 and Drive Isolation Transformers by SquareD/Schneider Electric
Special Transformers are available for both Non Linear (K4 and K13) and Drive Isolation applications
No to both questions. The UL K-Factor test evaluates temperature rise only. That is satisfactory for relatively passive applications such as computers and other office equipment loads. Drive Isolation Transformers are subjected to much more severe mechanical stress and thermal and mechanical cycling effects than K-rated Transformers. In addition, a motor drive`s K-Factor depends on the reactance of the line to which it is connected. In other words, the Transformer and the system, not the motor drive, determines the K-Factor. Therefore, choosing a universally appropriate K-Factor rating for a drive isolation Transformer is impossible. Most importantly, most K-Factor rated Transformers have insufficient reactance for proper drive harmonic control.
CTA-ID : 2002320