The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Transformers must be protected with properly sized Overcurrent devices such as Circuit Breakers and Fuses
Applies to Low Voltage Transformer products by SquareD/Schneider Electric
Overcurrents and Short Circuit events can damage Transformers and related equipment and wiring
NEC Section 450.3(B) requires, for Transformers rated 600 volts or less, that overcurrent protection be provided in accordance with Table 450.3(B).
Table 450.3(B) does not require overcurrent protection for the secondary of a Transformer if the primary current is 9 amperes or more and the primary overcurrent protection is limited to 125% of the Transformer rated current.
Table 450.3(B) permits primary overcurrent protection to be 250% of the Transformer rated current if the secondary current is 9 amperes or more and secondary overcurrent protection limited to 125% is provided.
The requirement for overcurrent protection for the secondary winding of a Transformer depends on the protection provided for the primary winding.
The overcurrent protection of the feeder conductors for the Transformer, if not larger than 250% of the Transformer primary current, may serve as the overcurrent protection for the Transformer primary winding.
Protection of the Transformer secondary conductors must be provided. Section 240.21(C)(1) through (6) provides the requirements for this protection.
The requirements for overcurrent protection for a panelboard supplied by the secondary of a Transformer are shown in 408.16(D).
Section: 450.3(B), Table 450.3(B), 240.21(C)(1) - (6), 408.
CTA-ID : 15441