Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
1. When using 1,2, or 3 pole ED,EG,or EJ branch mounted circuit breakers with a handle rating of 110 amperes
or less as branch devices, each bus connector will be restricted to no more that 170 amperes for the sum of the two breaker combination.
2. When using 1,2, or 3 pole ED,EG,or EJ branch mounted circuit breakers with a handle rating of 125 amperes
or less as branch devices, each bus connector will be restricted to no more that 145 amperes for the sum of the two breaker combination.
3. 125 and 250 ampere rated panels will be restricted to no more than 1 - ED, EG, or EJ two or three pole branch device. This device will be
restricted to the bottom 2 or 3 spaces of either side of the panel. All other restrictions apply.
a handle rating of 125 amperes
4. A maximum of 1 branch device over 110A allowed on 400/600 ampere panels in non-vented applications. (N3R,12,4,4X etc).
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!