Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Can key interlocks be used in conjunction with 1 pole branch breakers in an I-Line panelboard?
I line panelboards.
Products used in the United States.
No, only branch mounted 3 pole breakers or 2 pole breakers built in 3 pole modules can be used with key interlocks.
CTA-ID : 10060