Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Transformers are often called upon to provide electrical isolation between two sources of power
Applies to Low Voltage Transformers by SquareD/Schneider Electric
Isolation Transformer provide isolation between the primary and secondary winding. Autotransformers do not.
All of our standard Low Voltage dry type Transformers, except Autotransformers, are two winding Transformers. Any two winding Transformer that is not connected as an Autotransformer, either by the manufacturer in the factory or by the installer in the field, is an isolation Transformer. Electrical isolation is achieved by the electrical current in the primary winding causing magnetic flux in the core of the Transformer. In turn, the magnetic flux in the core induces electric current to flow in the secondary of the Transformer. Electrical isolation denotes that all of the electrical current flowing to the load is created in this manner. On the other hand, an Autotransformer only converts a portion of the electric current, with some of the electric current flowing directly from the source to the load.
Square D Digest listed buck boost Transformers are actually isolation Transformers that the installer field connects as an Autotransformer.
CTA-ID : 2000016