Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Mini Power Zone (MPZ) primary main breaker sizing
Applies to Mini Power Zone (MPZ) Transformers by SquareD/Schneider Electric
Main breakers for Mini Power Zone (MPZ) Transformers are sized per NEC 450-3b
The primary mains supplied with an MPZ can be replaced by a lower ampacity breaker of the same voltage & AIC ratings and style. Care should be taken not to install a new, lower ampacity breaker which will allow nuisance tripping due to Transformer inrush.
CTA-ID : 254