Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Are the FAL/FHL breakers DIN rail mountable?
FAL/FHL Molded Case Circuit Breakers
This would apply to unit mount breakers only it would not apply to I-Line breakers.
Want to be able to DIN rail mount the breakers in a panel.
No FAL/FHL breakers do not have a DIN rail mounting adapter available.
Powerpact H & J frame 3-pole breakers can be DIN rail mounted. Use kit # S29305.
DIN rail mounting kit (requires 15 mm depth on a 35 mm DIN rail)
Fits 3 pole module breakers only. (Not available in 2 pole)
See instruction bulletin, 48940-239-01.
CTA-ID : 3000