The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What branch connector is required to replace a Q1B circuit breaker with a QOB circuit breaker in an NQOB panelboard?
SK5668 is the bus finger or panel board connector kit for use when replacing a Q1B branch on the NQOB panel. The kit will accept QOB breakers. This is a 3 pole kit with A, B and C phase connectors. In a 225 amp NQOB interior this kit will allow you to mount 6-poles of breakers whether they are 1 pole, 2 pole or 3 pole breakers. In a 400/600 amp NQOB interior this kit will allow you to mount 3 poles of breakers whether they are 1 pole, 2 pole or 3 pole breakers.
CTA-ID : 767