Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What branch connector is required to replace a Q1B circuit breaker with a QOB circuit breaker in an NQOB panelboard?
SK5668 is the bus finger or panel board connector kit for use when replacing a Q1B branch on the NQOB panel. The kit will accept QOB breakers. This is a 3 pole kit with A, B and C phase connectors. In a 225 amp NQOB interior this kit will allow you to mount 6-poles of breakers whether they are 1 pole, 2 pole or 3 pole breakers. In a 400/600 amp NQOB interior this kit will allow you to mount 3 poles of breakers whether they are 1 pole, 2 pole or 3 pole breakers.
CTA-ID : 767
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!