The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
277V is sometimes necessary from a 240V source
Applies to Buck and Boost Transformers by SquareD/Schneider Electric
277V is a common voltage for Fluorescent Lighting Ballasts
Yes, Buck & Boost Transformers can be wired for 13.3% change to boost 240V to 272V using wiring diagram #4 in the Buck & Boost Transformer literature, or the Online Buck and Boost Calculator. See link below.
WARNING: This connection will usually result in both lines being `live`. Some 277V Fluorescent Lighting Ballasts and maintenance personnel who work on them expect one of the lines to be a neutral with insignificant voltage to ground. Load equipment damage or personal injury could result in such applications.
CTA-ID : 239