Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
For a floating array, the MPPT80 uses a wheatstone bridge to look for imbalance between PV- and PV+ to ground. 450kohms or less of impedance from PV- or PV+ to ground are enough to unbalance the bridge and cause a ground fault error signal.
Impedance of the bridge circuit is about 1.6Mohm.