The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Receive all the latest updates, news, and offers via Twitter.Follow us on Twitter
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What voltages can SDSA1175 be used on? Is it rated for a 120v single phase application?
single phase application
The SDSA1175 is applicable to 120/240Vac 1PH/3W systems. Use on a 120Vac 1PH/2W system is not recommended since the Indicating LED will not be functional on this system. The correct unit to use is the SDSA1175T for the 120v 2 wire circuit.
Two SDSA1175 may be applied to a 208Y/120Vac 3PH/4W system. Systems must be solidly grounded. Do not use the SDSA1175 on ungrounded systems.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!