Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The Controller LED Power Settings module provides control of the power settings for the controller LEDs. The state of the assigned coil register is the default state for the LED power. The time to return to the Default State is contained within the assigned holding register.
The registers are initialized with the current value of the module parameters on power-up, and when the Register Assignment is downloaded to the controller. Thereafter the module parameters are updated continuously with data read from the assigned registers.
Time in minutes to return to the default state. Default value is 5 minutes.
Using the Sample attached Telepace Studio program.
In a minute the LED power will turn OFF. To control the COM3 HMI power in the Scadapack 350 Defaul register is digital output register 11 and to monitor is address digital input 10013.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!