Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Only the Scadapack models 314, 334 and 357 (only AI on the 5606 Lower IO board) have register assignments that monitor the out-of-range status for analog inputs.
The only way to monitor if an analog input has failed, would be to monitor the raw input and look for a zero or full scale value.For a SP350 using a 5V/20mA register assignment and a 4-20mA input:
The screnshot below shows logic that scales the raw value of input 30001 to produce a scaled value in register 40110 (in mA)