Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
How to setup a PID on an ATV18 drive?
Altivar 18, ATV18.
Setting up PID to maintain level desired.
If you are using a 0-20mA or 4-20mA as your feedback then you will have to use AIC terminal.
With AIC is your feedback. There is no parameter in the drive that we can use to set your setpoint therefore you will need to use AI1 to set your setpoint. This will be a 0-10VDC to act as your setpoint.
Find L2A and set it to yes.
PID is not compatible with JOG or Preset speed functionality.
Go to LI2, L3, and L4 and set them all to OFF unless otherwise needed.
If a 4-20mA is used, go to AIC and set it to PIF.
Go to CRL and set it to 4.0 or 4-20mA or keep at 0.0 for 0-20mA.
If a 0-10VDC is used for feedback then set AI2 as PIF and ignore AIC and CRL.
Basically, AI1 (0-10VDC) is your setpoint on this drive.
As an example, if we have a transducer(4-20ma) 0-100PSi range with setpoint at 50 PSi you will need to set AIC as PI, CRL as 4.0, and adjust AI1 to 5 VDC since 50/100 PSI is same range as 5VDC/10VDC.