Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
8839MFD IEEE519 requirement
You would need a harmonic study. The M-flex (or any 6 pulse drive) would probably not meet IEEE519 with just a line reactor. However, since the harmonic noise is to be measured at the point of common coupling, which is the primary of the transformer from which the drive is powered, there is no way to be sure without actually doing the measurement as the transformer itself will filter much of this noise out. A passive filter (such as the matrix filter) on a 6 pulse drive, or the 18 pulse drive would probably meet IEEE519, but again would have to be measured for confirmation. It depends on the power system in question.