Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Single Phase application for SDSA
Surge Protection Device
Yes, by connecting two of the black leads to one phase and the other black lead to the other phase. (This application only works if the voltage supplied includes a neutral.) The white neutral wire must be connected to the grounded neutral. If there is no neutral used with the branch wiring, this surge arrester should not be used.
DO NOT CONNECT THE WHITE WIRE FROM THE SURGE ARRESTOR TO THE BARE OR GREEN WIRE.