Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
How can I change the high/low or on/off points on a 9013 pressure switch?
9013 pressure switches
It is sometimes necessary to change the pressure settings on the switches from what they have been preset
On all 9013 pressure switches there are one or two adjustment nuts holding a spring inside of the cover. With the power disconnected to the switch, these nuts can be adjusted to change the pressure switch. On units with one adjustment nut, this adjustment will change the high and low setting at the same time. On units with two adjustment nuts, the larger spring controls the high and low setting. The smaller spring controls the differential (spread) between the high and low points. Reference the attached troubleshooting guide for specific adjustment instructions.