Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What is the difference between the older D2 style contactors where aux contacts had to be specified and the newer LC1D contactors?
Crossing into new units from old units require a review of differences
The older D2 style contactors required a specification of needed auxiliary contacts. For example:
LC1D2501G6 would be an LC1D25 with 1 NC contact
LC1D2510G6 would be an LC1D25 with 1 NO contact
The newer contactors automatically come with 1 NO and 1 NC auxiliary contact. For example:
LC1D25G7 has 1 NO and 1 NC contact
The older contactors usually had a dedicated 60hz coil. This is designated by the 6 at the end of the part number. The newer contactors have coils designed for 50/60hz and are signified by the 7 at the end of the part number.