Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
How can you convert a Main breaker NQ442L2C panel to Main lug and keep the same MH50 box ?
Conduit piped already into MH 50 box
Change from Main breaker to Main lug Panelboard after installation of box
1) Remove the Main breaker kit and install a NQALM2 Main lug kit .
2) Install a 12" rail extension NQ12RDE kit to the Mains end of interior, and use the Blank Deadfront provided in the extension kit to cover Main lugs