The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
How can you convert a Main breaker NQ442L2C panel to Main lug and keep the same MH50 box ?
Conduit piped already into MH 50 box
Change from Main breaker to Main lug Panelboard after installation of box
1) Remove the Main breaker kit and install a NQALM2 Main lug kit .
2) Install a 12" rail extension NQ12RDE kit to the Mains end of interior, and use the Blank Deadfront provided in the extension kit to cover Main lugs