Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
What trip units are used in J and L frame mission critical breakers? I was looking in the following document: Short Circuit Selective Coordination for Low Voltage Circuit Breakers 0100DB0501, and it just says WU for the type, but does not tell me what trip unit that is used. Does it matter for selective coordination?
J and L frame mission critical breakers and trip units
Document: Short Circuit Selective Coordination for Low Voltage Circuit Breakers 0100DB0501 not clear on what trip unit is used.
It does not matter for selective coordination. Available mission critical trip units are:
J-frame: 3.2-W, 3.2S-W, 5.2A-W, 5.2E-W, 6.2A-W, 6.2E-W
L-frame: 3.3-W, 3.3S-W, 5.3A-W, 5.3E-W, 6.3A-W, 6.3E-W
Micrologic Electronic Trip Units In the Type column of tables covering PowerPact™ H, and J circuit breakers,
the “U” character in the third position stands for Micrologic Electronic Trip Unit.
• HDU360 - 3 pole 60A HD breaker with Micrologic trip unit.
• JLU3250 - 3 pole 250A JL breaker with Micrologic trip unit.
J- and L-Frame Mission Critical Circuit Breakers
In the upstream column of tables covering J- and L-frame mission critical
circuit breakers, there are “WU” characters in the third and forth positions
that stand for mission critical circuit breakers with Micrologic electronic trip units.
• JLWU–3 pole 250 A JL mission critical circuit breaker with Micrologic trip unit
• LDWU400–3 pole 400 A LD mission critical circuit breaker with Micrologic trip unit