Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Load center has two back fed breakers that need to be retained.
QO Load Centers
Back fed breakers are required by NEC to be retained.
Two, 2 pole breakers can be retained in Series S01 and S02 single phase QO Load centers. (Not available for Homeline)
This is done by using the Manual Transfer kit for the appropriate ampere rating, and not using the included QO2DTI interlock.
The table below outlines the choices;
|Load Center Type||Amperage Range||Series||Side of Panel||Position (in Panel)||Part Number|