The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Our 208/230 and 400/480V rated Altivar 61/71 drives do not require line reactors. However, depending on the voltage and power quality of the incoming power, a line reactor or other power conditioning device may be necessary in a given installation. Line reactors are used to filter and clean noisy power being fed into the drive. They also can lower the incoming voltage a few percentage points if your incoming voltage is running a little high so they are used on a case by case basis, as needed.
The ATV61/71 drives 100HP and below have an internal DC choke which handles a lot of the filtering and power conditioning. Drives rated 125HP and above have an external DC choke that ships separately and must be field installed. There is an option to use a 5% line reactor instead of this DC choke so in this case, a 5% line reactor would be mandatory on those drives 125HP and above if the customer decided to not use the DC choke. Either the DC choke or the 5% line reactor must be used, but not both.
Altivar 61/71 drives rated at 575/690V 125HP and above require a 5% line reactor also, it must be used on these drives.