Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Will the EDPA fixed padlock attachment physically fit onto the EDB-EPD Ground Fault Circuit Breakers?
Applies to EDB, EGB and EJB circuit breakers with suffix EPD
Application of fixed padlock attachment EDPA
The EDPA cannot be installed onto an EDB-EPD ground fault circuit breaker.
The EDPA must be attached to the breaker using slots in each end of the breaker escutcheon.
Standard EDB circuit breakers without EPD suffix (series 2 and higher), have these slots (see picture A below).
EDB-EPD Ground Fault Circuit Breakers do not have these slots (see picture B below), so the EDPA cannot be attached.
Standard EDB Circuit Breakers without EPD suffix, series 2 and higher (slots)
EDPA can be used.
EDB-EPD Ground Fault Circuit Breakers (no slots)
EDPA cannot be used.