Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
S-Flex 212 drive is going into SC3P fault on power up. What can cause this to happen?
Altivar 21, 212, S-flex
Any 21, 212 and S-Flex
Drive is detecting a ground short or a motor short circuit on the output of the drive.
-OC3P= means you are getting a ground fault. Its as short circuit or ground fault during constant speed operation.
-Try turning off the OPL F605= 0 and running the drive open circuit at 20hz 40hz and 60hz. Using a Fluke digital RMS meter measure the output voltage from the drive to see if they are balanced at each level.
If the drives output voltages are ok
-Try dropping the motor leads and megger out the motor leads and cables with a 1KV megger.
Check your grounding connections
- Double check all of you motor parameters settings in the drive.