The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Can you run the ATV12H037F1 drive with a motor that will pull 2.9 amps FLA?
Needs to run the drive continuous at 2.9 amps but the drive is only rated for 2.4 amps.
2.4 amps is the max continuous current rating for this drive. It does have a max transient current rating for 60 seconds at 3.6 amps but it does not allow for continuous current.