Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
What would cause the shunt trip breaker to trip on the Enclosed ATS46 and ATS48 soft starters on power up?
Enclosed Altistart ATS46, ATS48
Circuit breaker disconnect is tripping on power up.
The fault relay has a timed on-delay contact that will power the breaker shunt trip coil if the Altistart R1 relay is not opened by the end of delay. The factory sets the delay to 2sec. If the delay is set too short or the fault relay does not actuate, the shunt coil will energize and trip the breaker. Consult factory wiring schematics.
Consider increasing the delay time on the time delay relay.
If the relay circuits operate properly, consider that the thermal or magnetic elements of the breaker may be tripping it, rather than the shunt coil.