Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
PowerpactH J L Breakers
Yes,, the catalog number for the 80% rated breaker has “T” in the 9th character space.
The catalog number for a 100% rated breaker uses “R” in the 9th character place. For example, HDL36015T or HDL36015R or LGL36400TU31X or LGL36400RU31X).
100% rated H- and J-frame circuit breakers have copper lugs and can only be used with copper wire.
More information on field-interchangeable trip units in the Powerpact H, J, and L Frame breakers can be in the 2012 Supplemental Digest