Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Some three-phase generators have two sets of independent output windings per phase which can be reconfigured in several different ways. These types of generators are sometimes referred to as '12-wire' generators as there are 6 windings/coils with 2 wires each.The wiring on these types of generators can be configured in a method known as 'double-delta', which will provide single/split-phase phase power, with each leg 180 degrees out of phase. This should work with split-phase XW series inverters. A sample phasor diagram of a 12-wire generator in double delta is shown below. Please refer to the generator manufacturer for detailed documentation for a specific generator.
Note that 3-phase generators which only have one set of windings (sometimes called 4 or 6 wire generators) cannot be configured in this manner and cannot work with a split-phase XW inverter system.