The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Customers developing custom Xanbus monitoring applications will often ask for the Xanbus pinouts in addition to the Xanbus PGN files.
Xanbus network cables use an RJ45 connector wired to T568A Standard. Below are the pinouts for both Cat5 and Cat5e cables (note that the wire colors are different depending on which cable is used).
Pin Number Conductor Name Cat5 Wire Color Cat5e Wire Color
1 NET_S WHITE/GREEN WHITE/ORANGE
2 NET_S GREEN ORANGE
3 NET_C WHITE/ORANGE WHITE/GREEN
4 CAN_L BLUE BLUE
5 CAN_H WHITE/BLUE WHITE/BLUE
6 NET_C RANGE GREEN
7 NET_S WHITE/BROWN WHITE/BROWN
8 NET_C BROWN BROWN
The pins with names NET_S are DC Supply +15VDC (200mA must be provided for each Xanbus device on the network). The NET_C are DC Common. The CAN_L is CANBUS Data Low and the CAN_H is CANBUS Data High.