Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Many customers have run into communications problems when wiring multiple XW Xanbus devices into a network. Generally these issues can be corrected by a few simple steps, detailed here.
One of the more common occurrences is devices which are wired to the Xanbus network but do not show up on the System Control Panel. This is generally due to miswired Xanbus communications cables or missing network terminators. We have seen some larger systems, especially with multiple MPPT60 charge controllers, where the wiring and terminators are correct, but one or more MPPT60's do not display on the SCP. Restoring the MPPT60 settings to default has been know to correct this in many cases. If the system has three or more charge controllers, it may be necessary to remove one network terminator in order to boost the signal strength on the Xanbus network. Also, changing the order of the devices so that the SCP is located centrally in the device chain has also worked in some cases.