Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Do the Powerpact H and J frame breakers have interchangeable thermal-magnetic trip units?
Trip units can be changed on Powerpact H ,J and L frame breakers with the T or R suffix only. Trip units without the T or R suffix cannot be changed.
Circuit breakers with interchangeable trip units are marked Line and Load and CANNOT be reverse fed.
Note that interchangeable trip units are not possible on I-Line H and J breakers or on 2 pole breakers.
See Supplemental Digest or product catalog for more information.
*Available trip units for Powerpact H 60A frame
*Available trip units for Powerpact H 100 and 150A frames
*Available trip units for Powerpact J 250A frame
*Note that trip units grouped together in tables above are all interchangeable with other trip units in that table, but not with those in the other tables.