Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
NQ single phase
New or replacement
Use a QBL32100 with a NQMB2Q or HDL36100 or JDL26150 with a NQMBHJ or similar 3 pole breaker per the * footnote on p. 9-7 of the digest 176. The B phase lug on the breaker can be removed to avoid confusion. The bus links on the outer poles of the adapter kit and the deadfront cutout only works with 3p breakers.
Sign up for all the latest solutions, offers and best practices straight to your inbox.