The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
NQ single phase
New or replacement
With main breaker kit NQMB2Q, use a 2-pole Q-frame lug in, lug out breaker.
With main breaker kit NQMBHJ, either a 2-pole or a 3-pole breaker can be used for the higher interrupt H-frames, but if the interrupt is HD or HG, a 3-pole H-frame breaker must be used. This is because the bus links on the outer poles of the adapter kit and the deadfront cutout only work with 3-pole breakers (for higher interrupt values, such as HJ and HL, the 2-pole breaker already uses a 3-pole frame). In this situtaiton, the B phase lug on the breaker can be removed to avoid confusion.