The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Can an I-Line II busway run be separated in the middle?
Maintenance or Repair
Busway sections can be removed without disturbing adjacent sections of busway by removal of the joint pack.
Joint packs can be removed from the busway by loosening the 1/2" dia. torque bolt(s) as loose as possible without backing out of the nut retained on the opposite side and removing the #10 screws that hold the joint pack onto the busway duct top.
Lightly tap joint pack out from the side.