The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Adding 3p breakers to an NQOB
The kit has A , B and C phase connectors and screws and the A & C are symmetric. The latest version with hex head B phase connectors is very difficult to install if not impossible. Due to the close proximity of the plastic insulators on either side of the connectors, there is no room for a wrench or nut driver. Perhaps by inserting a screw into the top of each B phase connector , they can be slowly driven into position . Turn one hex head standoff 1/4 turn , then the other 1/4 turn , and repeat the process until they are both tight. Then install both breakers together . Here are the directions written on the envelope of the SK5668:
Replacing the interior with an NQ in the existing box or a complete panel changeout to a new NQ package is most likely the best choice. Another option is to find an old SK5668 with round standoffs.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!