Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Can a PHG36030G be retrofitted with a HJL36060 breaker at 60 amps . Also, can a PHG36100G be retrofitted with a 200a JJL breaker?
Breaker Bus Plugs
Yes, an HJP36060 or HJL36060 or similar can fit in place of a 30a breaker . Labels are the only issue . Also, a JJP36200 or JJL36200 can be interchanged. Both Powerpact H and J breakers use the same size bus-plug box.