Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
How many pole spaces does the New Surgelogic/Surge Loc Branch mounted SPD take up in a Panelboard ?
TVSS / NQ Panelboards
New space saving branch mounted SPD device saves on box size height for integral mounting in the Panels
Integral TVSS devices required up to 18" in extra height to install, but the SurgeLoc SPD does not require additional enclosure height to mount.
The Surgelogic SPD requires 12 single pole spaces , 6 on each side, in NQ Panelboard interiors . Since 42 circuit and 54 circuit interiors require the same box size , ordering a the 54 circuit interior allows you to keep the 42 circuits and have the branch mounted SPD taking the remaining 12 spaces. This allows the original 42 circuit amount of branch breakers needed as well as the integrated Surgelogic TVSS SPD Device