Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Display shows "Precharge Fault"
All models and serial numbers
Precharge failure: capacitor precharge relay fault
When the unit is powered up, the capacitor charging is monitored. When the capacitor voltage reaches 450 VDC, a 500 msec (for drive controllers ATV66U41N4
through ATV66D12N4) or 1500 msec (for drive controllers ATV66D16N4 through ATV66C19N4) timer is triggered.
While the timer is running, the voltage to the capacitor terminals must remain stable for 100 msec, otherwise a precharge failure fault is triggered
During operation, if the charging relay opens when RUN (LI1) is validated, a precharge failure fault is triggered. The check is made every millisecond.
If a precharge failure occurs, possible causes are:
• Failure of precharge relay/contactor or its associated coil drive circuitry.
• Control card ribbon cable incorrectly connected.
• Excessive mains voltage distortion.