Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
How do we access the coil in the 9-38A rated D line contactor for replacement or inspection?
TeSys D line contactors
9-38A TeSys D line contactors
Access the coil for replacement in D line contactors.
In order to access the AC coil you will need to use a small screw driver to press in the tabs located halfway down the top and bottom of the contactor. This will release the back of the contactor so that you can remove the old AC coil and insert the new coil.
DC coils are not serviceable. TeSys D line contactors with DC coils must be disposed properly in accordance with End-of-Life documentation found here:
AC Coil Replacement Instructional Video:
DC Coil End-Of-Life Video: