The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Shunt trip breaker is tripping
ATS22 Soft Start
Motor Control Centers using an ATS22 Soft Start with a shunt trip breaker
Time delay relay is set to the wrong time.
Increase the time on the time delay relay. This relay is used to delay the energization of the shunt trip coil when the bucket is powered ON. The shunt trip coil must not be allowed to energize until the normally closed trip relay on the soft start has time to open. Also, if the ATS22 goes to a faulted state, the shunt trip will trip the breaker.