The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric USA Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
For an existing breaker with a door-mounted rotary handle, if the rotary handle needs replacing, will the direct-mounted rotary handle fit into the same place?
Powerpact H, J, L, and P
While the Direct-Mounted and Door-Mounted Rotary Handles may appear very similar, there are differences in how they mount to the breaker.
No, the Direct-Mounted Rotary Handle will not fit onto the shaft of an existing Door-Mounted Rotary Handle. The reason is due to how they are installed onto the breaker.
DIRECT-MOUNTED ROTARY HANDLE DOOR-MOUNTED ROTARY HANDLE
Consists of one part: Rotary Handle Consists of three parts: Rotary Handle, Shaft, Base
Attaches to the face of the breaker itself (no shaft) Attaches to panel door, shaft connects to breaker