The smart thermostat, made Wiser.Learn more
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Situation 1, The motor runs the wrong direction from the drive (AFC) and bypass both.
Resolve this situation by swapping 2 of the motor leads where they connect to the output of the drive system.
Situation 2, The motor runs the wrong direction in bypass but the correct direction in drive (AFC).
Resolve this situation by swapping 2 of the incoming power leads where your main power connects to the disconnect of the enclosed product.
Situation 3, The motor runs the correct direction in bypass but the incorrect direction from the drive (AFC).
Resolve this situation by swapping 2 of the motor leads AND 2 of the incoming power leads.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!