Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
E-Flex drive is blowing the secondary fuse of a control transformer. What are some possible causes?
A possible short circuit in the control circuit
Check bypass, DOC, and IS contactors.
Ohm out all relays and contactors
Check any user supplied contactors. Make sure only a dry contactor between pins 6 & 7