Start here for access to our Knowledge Base to get answers to over one hundred thousand questions online in seconds.Find Answers
...See what we've been doing in some of our major markets.Find your Location
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
E-flex would not pull in the line contactor (B09) . What are some possible causes?
All serial numbers for ATV61
Possible open circuit or contactor
Check to see if the line contactor will pull in, in the "test" mode (test/normal switch)
Check that the drive is getting a run command (contactor closes with the command)
Check all wirings for any loose connections.
Check the control wiring for loose/open connections.
If more assistance is needed contact Drives Technical Support Group.